Energy saving integrated lighting and HVAC system

ABSTRACT

This invention integrates energy saving lighting with energy saving HVAC (Heating, Ventilating and Air Conditioning). This system is termed by the inventor “ILAC” (Integrated Lighting and Air Conditioning). An ILAC system includes light fixtures mounted in a ceiling and, emitting lamp heat into a plenum and visible light into a room. A central computer controls both lighting and HVAC systems. In a COOL mode an HVAC unit cools the room through a supply air duct and return air duct and the lamp heat exits the plenum through an exhaust duct. In a HEAT mode the HVAC heats the room through the same supply air duct, a ceiling-to-plenum duct carries the heated room air into the plenum, and an HVAC return air duct carries room and plenum heat back into the HVAC unit that uses less power to heat the lamp-warmed return air. In a thermostat-controlled OFF mode, warm room air convects through the ceiling duct into the plenum and exhausts through a plenum exhaust duct along with lamp-heated plenum air. Optionally, plenum exhaust duct may include a radiator to transfer plenum heat to pre-heat water entering a remote hot water heater.

US PATENT REFERENCES CITED

7,223,002 - Miller, et al 5,384,881 - Miller, et al. 7,209,870 - Simmons, et al 5,303,125 - Miller, et al. 7,188,481 - DEYoe, et al 5,268,977 - Miller, et al. 7,177,534 - Jones, et al 5,099,399 - Miller, et al. 4,105,276 - Miller 5,486,984 - Miller, et al. 5,099,399 - Miller, et al. Des.267,978 - Miller 7,172,132 - Proffitt, et al 4,178,525 - Miller 6,402,349 - Miller, et al 5,967,653 - Miller, et al 5,907,648 - Miller, et al 6,582,104 - Miller, et al

NP (NON-PATENT) REFERENCES

NP-1 New Technology, Power Systems News, L.A. Dept of Water & Power, July 1993

NP-2 Museum Lighting the Next Generation, Exhibit Builder magazine, August 1993

NP-3 New lamp Halves Energy, Progress, Pacific Gas & Electric, L.A., CA, March 1977

NP-4 The Energy Conservation Collection, Johnson Industries 1992

NP-5 Tri-Mizer 3-way Energy-Saving Bulb, Ad, Creators, Inc. 1993

NP-6 Tomorrow's Lighting Today (circline lamps), Montgomery Ward Ad. 1992

NP-7 Field Demonstration, Lighting & HVAC Cost Savings, Energy Ctr, WI, January 2005

NP-8 Daylighting and Architetecture, Waldron Lighting Design, PA, March 2007

NP-9 Commercial Rebates & Financial Assistance, Alameda Power, CA July 2007

NP-10 Building Efficiency (thru HVAC efficiency) Johnson Controls, Inc WI. May 2007

FIELDS OF THE INVENTION

This invention relates to the fields of lighting and air conditioning, and to the field of energy conservation in public, commercial and residential buildings.

BACKGROUND OF THE INVENTION

Historically, lighting has been specified by engineers in the IESNA (Illuminating Engineering Society of North America) and air conditioning has been specified by ASHREA (American Society of Heating, Refrigerating and Air-Conditioning) engineers. These diverse practitioners have independently tried to design their respective systems within buildings being designed or already designed (or worse yet already built) to the drawings and specifications of architects of the AIA (American Institute of Architects). A popular architectural trend is the attempt to save lighting energy through “daylighting” (big windows and skylights). The result is poorly controlled daylight that requires energy for separate day-time supplementary use, as well as a complete night-time lighting system. However, double-pane windows and skylights transmit eight times more heat (in or out, depending on the season and weather) than insulated walls or ceilings. Thus savings in lighting energy is often overwhelmed by increased HVAC energy use.

Even in well-insulated buildings with few windows and no skylights, the cost of energy use continues to rise. Both Residential and commercial customers are experiencing dramatically increasing lighting and HVAC costs. Lighting itself averages about 32% of a typical commercial building's energy use, and lighting-plus-air conditioning power (to remove heat generated by the lighting) comprise more than half of most building's total energy load. Thus lighting and HVAC designers (who usually work at different companies in different cities) need to work together to specify energy-saving, effective, integrated lighting and HVAC systems within the architectural designs of proposed, new and old buildings.

It is a well-known fact that all light sources emit many times more IR (infrared) and UV (ultraviolet) watts energy than visible light watts. It is also a well-known fact that it takes about 3.5 watts of air conditioning to remove a watt of lighting heat. Further, in a heating mode it takes 3.4 watts of HVAC heat to emit one watt of heat into a room.

INCANDESCENT LAMPS: Incandescent lamps have changed very little since the carbon-filament, vacuum-filled light bulb was invented 100 years ago by Thomas Edison. It is said that Edison invented a very efficient electric heater that produced 96% infrared heat and emitted only about 4% visible light. Modern tungsten/halogen versions of Edison's lamp still produce only about 6% of their energy as visible light, with the balance almost entirely invisible IR and about 1% UV (ultraviolet). That means a lamp consuming 100 watts, produces 94 watts of UV and IR that contribute nothing to vision, but contribute only to whatever (and whomever) they encounter.

Using the average of 3.5 watts of air conditioning to remove each watt of heat, it takes 3.5 (100)=350 air conditioning watts to maintain room heat balance for each 100 watt lamp, plus the 100 watt lamp load, means a 100 watt lamp with HVAC uses 450 watts. Although incandescent lamps are inefficient in terms of lumens-per-watt, they remain popular because of their light quality. They have a continuous, uninterrupted visual spectrum, or CRI (Color Rendition Index) providing light that the human eye can most efficiently see.

FLUORESCENT LAMPS: Considering integral ballast losses, fluorescent lamps (including compact fluorescent screw-based lamps) are about 3 times more efficient in lumens-per-watt than incandescent lamps, so the light output becomes 6%×3, or about 18% of total lamp energy (instead of 6% for incandescent lamps). Thus they emit 82% heat, and it still takes that 3.5 watts of HVAC to remove a watt of fluorescent (even compact fluorescent) lamp heat. Non-Patent referenced NP-1 through NP-6 show the applicant's familiarity with the properties of florescent lamps. METAL HALIDE H.I.D. LAMPS: HID (High-Intensity Discharge) lamps, such as metal halide lamps, have replaced many incandescent lamps, because they are more efficient in commercial buildings. However, like fluorescent lamps, they emit 5 times more IR than visible light, and it still takes about 3.5 watts of air conditioning to remove a watt of lamp heat. LIGHT EMITTING DIODES: Popular, promised solutions to lamp heat have been the more recent introduction of LED's (Light Emitting Diodes) that are more compact than even the “compact” fluorescent lamps. The tiny LED itself runs cooler, but the LED power supplies still emit that same 5 times more IR than visible light.

Also, LED solid-state lamps have the same problem as gas-discharge lamps. They have low CRI (Color Rendition Index). When colors seen by the human eye are distorted by poor light quality, more light is required for vision. In simplest terms, if you turn off the lights, you see nothing; and if you turn on ugly, distorted light colors, you see ugly-colored objects that human eye retinas have trouble imaging. That's why many residential and commercial customers continue to use incandescent light bulbs.

LIGHT SOURCE SUMMARY: It is a basic fact that all light sources, including incandescent, fluorescent, HID and LED lamps, emit from 5 times to 20 times more IR (infrared) watts than visible light watts. The UV and IR are the primary cause of skin discomfort, eye strain and eye damage, as well as photochemical damage to everything from carpets and textiles to food displays. The current I.E.S.N.A Handbook published in 2000, states: “UV and IR do not contribute vision, but only contribute to damage, and thus should be avoided.” The publication of that information resulted from the applicant's development of NoUVIR® (NO UV or IR) light fixtures in 1992, the filing date of applicant's U.S. Pat. No. 5,099,399 for a fiber optic light projector. Thus “NoUVIR” became the registered trademark of NoUVIR Research Company, founded by co-inventors of the U.S. Pat. No. 5,099,399 patent, Jack V. Miller and his daughter, Ruth Ellen Miller. The recent 2007 issue of U.S. Pat. No. 7,223,002 for hybrid light fixtures makes it now possible to integrate NoUVIR general illumination lighting with HVAC, the subject of the present invention.

BRIEF DESCRIPTION OF THE DRAWINGS

FIG. 1 is the Relative Spectral Sensitivity of the human eye.

FIG. 2 is the total SPD (Spectral Power Distribution) of an incandescent lamp, including the UV and IR bands.

FIG. 3 is an applicant's prior art fiber optics projector of patent U.S. Pat. No. 5,099,399 that emits no UV or IR energy in the projected light.

FIG. 4 is the fiber optics projector of '399 patent using several types of fiber optic luminaires in a ceiling.

FIG. 5 is a drawing of the visible SPD (Spectral Power Distribution) of the fiber optic projector of FIG. 3, showing visible light, with no UV or IR.

FIG. 6 shows light fixtures of patent U.S. Pat. No. 7,223,002 mounted in a ceiling.

FIG. 7 shows a fluorescent fixture above a luminous ceiling including patent U.S. Pat. No. 6,402,349, mounted on suspended ceiling T-bars.

FIG. 8 is the total SPD (Spectral Power Distribution) of a fluorescent lamp, showing visible light, as well as UV and IR.

FIG. 9 is the total Spectral Power Distribution of a metal halide lamp, showing visible light, as well as UV and IR.

FIG. 10 is the total Spectral Power Distribution of an LED (light emitting diode), showing its visible light, as well as UV and IR.

FIG. 11 is an illustration of a lamp showing its visible light, as well as UV and IR, irradiating a thermostat mounted on a wall.

FIG. 12 is a drawing of the energy-conserving ILAC (Integrated Lighting and Air Conditioning) system according to the present invention with the HVAC unit in the “COOL” mode wherein a number of controllable dampers direct flow through selected air ducts.

FIG. 13 is a drawing of the energy-conserving ILAC system according to the present invention with the air HVAC unit in the “HEAT” mode.

FIG. 14 is a drawing of the energy-conserving ILAC system according to the present invention with the HVAC unit in the “OFF” mode during warm weather.

FIG. 15 is a drawing of the energy-conserving ILAC system according to the present invention with the HVAC unit in the “OFF” mode during cool weather.

FIG. 16 is a drawing of the energy-conserving ILAC system according to the present invention, showing a detail of the utilization of a waste heat in a plenum exhaust air duct.

FIG. 17 is a block diagram of the energy-conserving ILAC system according to the present invention.

DETAILED DESCRIPTIONS OF THE DRAWINGS

In FIG. 1 the Relative Spectral Sensitivity of the human eye is shown as the C.I.E. (Commission International de'l Eclairage) curve represented by the broken line. Since a light meter is intended to indicate the light level that a human can see, the light meter sensitivity is shown as a solid line. The visible spectrum of the eye extends from the UV (ultraviolet) threshold at 380 nm (nanometers wavelength) to the IR (infrared) threshold at 770 nm. Thus the human eye (and the light meter) are both designed to indicate visible light intensity as the area under the C.I.E. curve, wherein light of wavelengths shorter that 380 nm or longer than 770 nm do not produce a visible retinal image in the eye, and are not measurable with a light meter.

In FIG. 2 the full spectrum of an incandescent quartz/halogen lamp is shown including UV down to 100 nm and IR extending to 4500 nm. It may be seen that the area (energy) under the C.I.E. (visible light sensitivity) curve is only about 8% of the energy under the curve of the total energy emitted by the lamp. This shows that except for a few percent of UV energy, about 90% of the lamp energy is IR (invisible heat) that does not contribute anything to vision, but does contribute to the air conditioning load. In order to illustrate the extent of the IR energy, FIG. 2 also includes the SPD (Spectral Power Distribution) of an electric frying pan operating at 350° F.

Human vision is produced in the eye by light passing through the lens and iris (the pupil) and projecting an image onto the retina. As shown in FIGS. 1 and 2, the retina can see only the light with wavelengths between 380 and 770 nm. However, the pupil responds to both UV and IR energy by reducing the iris diameter to protect the retina from damage. Since visible light on the retina is proportional to the area of the iris, removal of UV and IR opens the iris like the f-stop of a camera to produce a brighter retinal image. Thus light without UV or IR provides better vision with less light energy. This was demonstrated in 1993 by a conservator in the Gene Autry Museum in Los Angeles, Calif., where two similar water-color paintings were illuminated side-by-side. One painting was illuminated with a tungsten/halogen museum track light, and the other with light from a NOU(VIR® fiber optic system.

The lights in this demonstration were first adjusted to equal intensity in footcandles, measured with a light meter. The painting illuminated without UV or IR appeared substantially brighter, so it was optically dimmed (without lowering the color temperature) so both paintings appeared equally bright to the observers. Then the respective light levels were measured again, wherein the NoUVIR footcandle level was approximately half the measured footcandle intensity of the tungsten-halogen tracklight.

The elimination of UV and IR allowed the observers' irises to enlarge and admit more light. A test gallery installation was sponsored by the local electrical utility, and was certified by their engineers as saving 70% of the power used for illumination. In an article in Exhibit Builder Magazine, non-patent reference NP-2, the museum design specialist responsible for a full-gallery demonstration states: “The . . . gallery . . . is perceptibly cooler than other areas of the museum.”

FIG. 3 shows the above NoUVIR fiber optic projector of the Miller, et al (Jack V. Miller and Ruth Ellen Miller) patent U.S. Pat. No. 5,0900,399 that emits zero UV or IR energy. It has been marketed under the trade name “Cold-Nose®” fiber optic projector, used in many museums to protect artifacts from photochemical damage for over 10 years.

In FIG. 4 a fiber optics illumination system is shown including the light projector (1) of Miller, et al '399 patent in the ceiling of a room-size museum exhibit case. The projector is mounted above the ceiling and transmits its visible light into the room through optical fibers (2) and fiber optic luminaires (3), as described in Miller, et al U.S. Pat. Nos. 5,486,984; 5,268,977; 5,303,125; 5,384,881 and 5,907,648. Thus all lamp heat is emitted above the ceiling and only cold light (6% of the lamp energy) without UV or IR is emitted into the room. Thus 94% of the lamp energy is emitted outside the exhibit case.

In FIG. 5 a drawing of the visible SPD (Spectral Power Distribution) of the fiber optic projector of FIG. 3, shown without UV or IR. A series of successive filters remove all UV and IR, leaving only the visible light between 380 to 770 nm. Since the highly-transmissive Pmma (Polymethyl methacrylate) plastic fibers are subject to melting under intense, focussed IR, removal of the heat from the fiber optic projector light source prevents fiber damage, whereby fibers may be warranted for 10 years without yellowing or losing transmissivity. This NoUVIR SPD has also been shown to extend the lives of photosensitive articles, like documents and textiles, three to eight times longer than conventional light sources. It should be noted that FIG. 5 includes the SPD of direct sunlight, showing the continuous, uninterrupted spectrum producing ideal CRI (color vision). The solar SPD peaks at 560 nm, the green (most easily seen) shown in FIG. 1. It is not important whether one believes humans were evolved or designed with vision perfectly suited for efficient hunting and foraging in green fields and forests. However, it is very important the most efficient lighting should replicate the spectrum of sunlight.

FIG. 6 is the light fixture of U.S. Pat. No. 7,223,002, shown in several mounting configurations in a ceiling. The thermal properties are similar to those of applicant's '399 patent, but conventional optical fibers (2) extending from fiber optic projector (1) of FIG. 4 of the '399 patent are not used. Instead, the same heat-removing optical element (a thick, fiber-like rod) used in fiber optic projector (1) is used to absorb heat from the intense focussed light and dissipate it into the plenum above a ceiling. Thus the invention of the '002 patent is entitled “hybrid” fiber optic luminaire.

FIG. 7 shows a fluorescent light fixture (4) in a luminous (light-transmitting) ceiling on which an upper transparent acrylic lens (5) of U.S. Pat. No. 6,402,394 is spaced above a lower diffusing lens (6). The pair of lenses with an airspace (7) therebetween rests on the horizontal portions of suspended-ceiling T-bar beams (8). A horizontal reflector (9) is mounted on ceiling T-bar runners (8) spaced above the lenses. A light source emitting visible light, plus UV and IR, is mounted under the reflector. The light source shown in the '394 patent is a pair of straight-tube fluorescent lamps, but FIG. 7 shows a spiral compact fluorescent lamp (10). However other lamps; metal halide, incandescent or even LED's may be used, providing they do not emit high IR that could melt the plastic lenses. Then visible lamp light passes through the lenses, but IR and UV are blocked.

In FIG. 8 the full spectrum of a fluorescent lamp is shown, including about 18% visible light (shown in the form of narrow spikes) in the band between 380 and 770 nm wavelength, 6% UV and approximately 76% (depending on configuration and manufacturer) IR (including ballast losses shown in typical black body distribution). It is well known by lighting scientists that the retina of the human eye has three types of color sensing cones, each respectively sensing “RGB” (Red, Green and Blue) light. This “tri-stimulus” lamp priciple, uses eye-sensitivity peaks at the respective RGB wavelengths of red light at 650 nm; green light at 550 nm and blue light at 450 nm to match the color sensitivity of the cones of the human eye. The RGB principle is also used for phosphors in color TV screens, computer monitors and cell phones.

However, in addition to the visible RGB light, the full spectrum of the fluorescent lamp also includes the UV energy, having wavelengths as short as 150 nm, and the IR heat having wavelengths longer than 770 nm, extending past 6000 nm. Those invisible are acknowledged by the I.E.S.N.A. as contributing to damage to museums artifacts, retail merchandise, and even foods.

In FIG. 9 the SPD of a metal halide High-Intensity Discharge (HID) lamp is shown having approximately 76% IR output. Thus a standard 40 watt lamp emits 30 watts of IR heat, and each watt must be removed with 3.5 watts of air conditioning. Also it can be seen that (as in fluorescent lamps) there are high UV emissions from such lamps. Damage caused when a UV photon is absorbed by an atom of a molecule. The entering photon changes the valence electron ring of an atom and thereby alters the chemical structure of the molecule. This transition produces heat as well as chemical changes, as anyone knows who has experienced a painful case of sunburn.

In FIG. 10 the SPD of a Light-Emitting Diode (LED) lamp is shown having approximately 76% IR output that must be removed with 3.5 watts of air conditioning power. Also, it can be seen that SPDs (as in fluorescent lamps and HID lamps) show high UV. Although the UV spikes are narrow, they comprise very energetic, deep radiation that can cause severe fading and structural damage when absorbed by photosensitive objects.

FIG. 11 is an illustration of a lamp within a room and showing its visible light, as well as UV and IR, irradiating a thermostat mounted on a wall. In this illustration a “PAR lamp” (Parabolic Reflector lamp) (11) is shown in a “top hat” recessed fixture (12). This is a widely-used combination in both residential and commercial buildings. A portion of the lamp IR is absorbed into a thermostat (13) and all the wall and floor surfaces (14) to cause the thermostat to sense the radiant IR heat instead of the room air temperature. Thus the room may easily be an ideal 68° F., but the thermostat “thinks” the room is 72° F., several degrees warmer than it really is. That initiates HVAC cooling when the room air is already at a comfortable temperature. Then the HVAC cooling continues over a time lag period until the thermostat and room surfaces cool to the set air temperature.

In addition to the thermostat, human skin is also sensitive to IR radiation. Thus the girl in the summer dress in FIG. 11 doesn't really care what the thermostat says. She feels the IR on her skin and responds by turning down the temperature setting of the thermostat. She and the thermostat both agree that the room is “too hot”.

Therefore, in order to have accurate room air temperature to control an HVAC unit, all IR should be excluded from the room lighting. The girl in FIG. 11 also calls attention to the fact the ILAC term includes “Integrated Lighting” as well as HVAC. That includes the need for occupancy data as described below and shown in FIG. 17, to reduce the lighting to an OSHA minimum of 1.5 fc in unoccupied spaces. These effects may not appear as major factors, but every improvement in ILAC efficiency results in an incremental power saving.

In FIG. 12 the energy-conserving ILAC system according to the present invention is shown with the HVAC (15) unit in the “COOL” mode. In this mode the thermostat (16) is set to cool the room to a desired room temperature. The optimum HVAC energy efficiency is obtained by isolating the IR heat (17) from lamps (18) in the plenum (19) above the ceiling (20) of a room (21). Each lamp (18) is provided with a thermal barrier (22) so only cool visible light (23) enters the room. The HVAC unit (15) cools the room air by blowing cool air into the room through a supply air outlet (24). Blower-driven air flow is designated by several parallel arrows.

Ceiling air damper (25) is closed, so warm room air returns to the HVAC unit through an open return air damper (26) from near the ceiling and on through return air inlet (27). The HVAC unit cools the air and its blower (28) blows the cool air back into the room through supply air outlet (24). However, the lamp heat in the plenum is vented by convection (designated by a single arrow having a “C”) from the plenum through open damper (29) of a plenum exhaust duct (30).

In FIG. 13 the ILAC system according to the present invention is shown with the HVAC (15) unit in the “HEAT” mode with thermostat (16) is set to HEAT. Optimum HVAC efficiency conserves the IR heat (17) from lamps (18) in plenum (19) above ceiling (20) of room (21). Ceiling air damper (25) is open, so warm room air enters plenum (19), mixes with and receives the heat of light (17) and returns to the HVAC unit through open exhaust/return air damper (29) into return air inlet (27) of HVAC unit (15). The HVAC unit further heats the warm plenum air, and blower (28) blows warm air into the room through supply air outlet (24). The lamp heat in the plenum is precluded from being exhausted by exhaust/return air damper (29), closing off plenum exhaust duct (30) and causing the warm plenum air to enter the HVAC unit through the return air inlet (27).

FIG. 14 shows the ILAC system according to the present invention with the air conditioner unit (15) in the “OFF” mode during warm weather. This may be a manual setting of thermostat (16) or may be an HVAC quiescent time in which the thermostat is at the set temperature wherein there is no command to either heat or cool the room. In this mode the optimum energy efficiency can be obtained by allowing warm room air to convect into the plenum through the open ceiling air damper (25) to mix with the lamp heated air in the plenum and convect out through the open exhaust/return air damper (29) into and through plenum exhaust duct (30). The convection may be facilitated by an exhaust turbine (31). Some convection make-up air may be allowed into the room through an open door, window or outside air inlet vent (not shown), or ceiling air damper may be set slightly open to external air as as shown to facilitate convection. In an optional mode, the HVAC unit (15) does not heat or cool, but the fan (27) may be turned on to circulate room air through room air return damper (26) and HVAC unit (15).

FIG. 15 shows ILAC system according to the present invention with the air conditioner unit (15) in the “OFF” mode during cool weather. This may be a manual setting of thermostat (16) or may be an HVAC quiescent time in which there is no thermostat command to either heat or cool the room.

In a first HVAC system-off mode, heat energy in the room can be conserved by preventing the warm room air from convecting into the plenum by closing ceiling air damper (25). Room air warmed by occupants (who radiate approximately 300 watts each) is convected upwards and through room air return damper (26). The warm room air can then subside down through the HVAC unit (15) to re-circulate into the room through the HVAC supply air outlet (24). In this first system-off mode, lamp heat is simply allowed to convect out through plenum exhaust duct (30).

Greater utilization of a waste lamp heat may be obtained using a heat-exchange radiator (32) in plenum exhaust duct (30). The radiator water inlet (33) is supplied with cold (unheated) water. The cold water is heated by plenum exhaust air and is routed as warm water (34) heated by lamp heat to the water supply of an appliance, such as a hot water heater (35). Thus the hot water heater starts its heating with already warmed water, requiring less energy from heating element (37) to heat to the desired hot water temperature and route it through pipes (38) to one or more hot water uses (39). In a second HVAC unit off mode, lamp heat is utilized by closing the fan switch to operate in a fan-only mode. Then the ceiling air damper (25) is opened, allowing the fan do draw warm room air into and through plenum (19) and through exhaust/return air damper (29) which is moved to close off plenum exhaust duct (30) and open warm air flow to the HVAC return air inlet (27), whereby the fan, using very little power to slowly drive blower 28, re-circulates the warm room air, further warmed by the lamp heat, back through the room without energizing the HVAC heating element.

FIG. 16 is a drawing of the energy-conserving ILAC system according to the present invention, using the fiber optic lighting system as shown in FIG. 4. In the COOL mode shown in FIG. 16, thermostat (16) is set to cool the room to a desired room temperature. The optimum HVAC energy efficiency is obtained by isolating the IR heat (17) from lamps of one or more fiber optic projectors (1) in a non-air-conditioned space (designated 19 a as a plenum equivalent) separated from room 21 by an insulating divider (20 a).

Optical fibers (2) conduct light from projector (1), which includes a lamp (18) and a thermal barrier (22) as seen in FIG. 3. Each optical fiber (2) extends to one of a number of fiber optic luminaires (3) mounted in and from ceiling (20) of room (21). Since projector (1) emits no heat, fiber optic luminaires (3) emit only cool, visible light (23) into the room. This is a practical arrangement, since fiber optic luminaires are optically efficient because they can be individually aimed with beams that can be zoomed from narrow to wide beams, as shown in applicants's U.S. Pat. Nos. 5,486,984 and 5,268,977. They also can be mounted above, within or below ceiling (20) in any desired aesthetic design. The arrangement shown in FIG. 16 is also easily maintained. A single projector lamp can illuminate a variety of luminaire types and styles, simplifying lamp inventories. The lamp can be quickly changed at eye level, without a ladder, and from outside the occupied room.

The HVAC unit (15) cools the room air by blowing cool air into the room through a supply air outlet (24). Warm room air returns to the HVAC unit past closed room air return damper (26) and on through return air inlet (27). However, the lamp heat in the non-air-conditioned space (19 a) is vented by convection through open damper (29) of a plenum exhaust duct (30).

In an alternative mode with the HVAC unit OFF, the room air return damper (26) may be opened to convectively vent lamp IR heat (17) out through plenum exhaust duct (30).

FIG. 17 is a system block diagram of the ILAC (Integrated Lighting and Air Conditioning system) according to the present invention. A central computer (40) has command and feedback connections to at least one HVAC unit (41, 15-1 through 15-N). The central computer also receives input (42) from various sensor data, and produces output control commands to (43), operating system components. Central computer (40) provides commands for controlling lighting, as well as air conditioning. Optimum energy use should consider both occupancy and visual needs of the occupants. Thus individual lights may turned off or on by the central computer. or dimmed, as seen in applicant's U.S. Pat. No. 4,178,535 and non-patent reference NP-5.

BASE LINE EXAMPLE CALCULATION

To establish a simplified base-line cost example for conventional in-room lighting, a theoretical, small retail space (office, home or factory) is selected to be 48 feet wide×96 feet deep (multiples of 4×8 ft modules), was assumed to achieve average light levels with 100-watt lamps on 8 ft×8 ft centers (including perimeter rows). This is 7 rows of 13 lamps, or 91 light fixtures, consuming 9,100 watts of electrical power with downlights or tracklights. These calculations relate only to energy conservation through integrating lighting with HVAC units. Other heat transfer (in or out) through walls, windows and roofs, as well as as heat generated by occupants (who radiate 600 watts each) and other miscellaneous sources, such as computers, appliances, copiers, printers, TVs, etc. are ignored.

Cooling Energy Efficiency

Since it normally requires 3.5 watts of air-conditioner energy to remove 1 watt of heat from the room, the HVAC unit uses 3.5×9100 watts=31,850 cooling watts to maintain room temperature. Then, 31,850 watts×8 hours/day=254,000 (254 KWH) per day×30 days a month=7,620 KWH/month×$0.15/KWH=$1,143 a month to remove the heat of lighting from the room.

However, if lamp heat is isolated above the ceiling per the invention, the $1,143 power cost is saved, so the heat removal cost of $1,143×12 months=$13,716 is saved a year. Many buildings are insulated and/or have shared interior walls. Thus heat from occupants (300 watts each), plus heat from computers, printers, monitors, TV sets, copy machines, stoves, microwave ovens, refrigerators, etc., often requires year-round cooling.

Heating Energy Efficiency

The laws of thermodynamics are quite consistent, so it also takes about 3.5 watts of HVAC gas or electric heat to generate each watt needed to warm a room. In cold weather, the present invention functions as if the lights (and their heat) are inside the room. They simply become part of the heating system.

SUMMARY OF THE INVENTION

As the energy costs in buildings continue to escalate, the present invention dramatically reduces those costs of through ILAC (Integrated Lighting and Air Conditioning) by:

1. Reducing HVAC cooling load by excluding lamp heat from a room; 2. Lowering the HVAC heating load by recycling the lamp heat; 3. Improving occupant comfort without using additional power; 4. Utilizing lamp heat in other heating applications in the building; 5. Shortening HVAC cycles by managing light and heat; and 6. Reducing installed size, cost, ducting and power of HVAC units. 

1. An integrated lighting and HVAC (Heating, Ventilating and Air Conditioning) system for one or more rooms, each room (21) having a heat-insulating ceiling (20) separating each respective room from a plenum (19); at least one lamp (18) mounted in or above each ceiling, said lamps emitting lamp IR (17) into the plenum above the room and emitting only visible light (23), substantially without heat, through one or more thermal barriers (22), into the room; a number of ventilation ducts (24, 27, 30), connecting the rooms and one or more plenums to one or more HVAC units (15, 41), said ducts optionally having remotely operated dampers (25, 26, 29); and a central computer (40) operating said HVAC units (15, 41) and dampers (25, 26, 29) to control energy use (41, 43) based on environmental sensor inputs (42) and HVAC feedback (41).
 2. An integrated lighting and HVAC system according to claim 1 in which the environmental sensor inputs (42) are selected from the group including: room occupancy, room temperature, room humidity, plenum temperature, light status, outside air temperature; and the HVAC (41) performance feedback data is selected from the group including input air temperature, supply air outlet temperature, heater temperature, chiller temperature, air outlet humidity, air velocity and HVAC line voltage.
 3. An integrated lighting and HVAC system according to claim 1 in which the lamps (18) may be individually or collectively switched on, off or dimmed by the central computer (40) using occupancy sensor data or occupant function data.
 4. An integrated lighting and air conditioning system including: at least one light source (18) above a thermally insulative ceiling (20) separating a room (21) from a plenum (19), each said light source emitting heat (17) into the plenum above the room and emitting visible light (23) into the room; an HVAC (15) unit heating or cooling ventilation air; a supply air outlet (24) connecting the outlet of the HVAC unit to the room; a room air return damper (26) connecting said room to the a return inlet (27) of the HVAC unit; a plenum exhaust air duct (30) connecting said plenum (19) to external air the a ceiling air damper (25) connecting said room (20) to said plenum (19); a plenum exhaust/return air damper (29) connecting said plenum (19) to the a HVAC unit inlet (27); a thermostatic control (16) having at least three-positions including COOL, OFF, and HEAT, and an optional FAN switch; and a system of controllable dampers (25, 26, 29) controlling and circulating air from the HVAC unit through the room and plenum.
 5. An integrated lighting and HVAC system according to claim 4 in which the environmental sensor inputs (42) are selected from the group including: room occupancy, room temperature, room humidity, plenum temperature, light status, outside air temperature; and the HVAC (41) performance feedback data is selected from the group including input air temperature, supply air outlet temperature, heater temperature, chiller temperature, air outlet humidity, air velocity and HVAC line voltage.
 6. An integrated lighting and air conditioning system according to claim 4, operating in a COOL mode in which: while the thermostat (16) is in the COOL mode wherein a central computer (40) closes a ceiling air damper (25), and opens a room air return damper (26); whereby a blower (28) of the HVAC unit (15) circulates cool air through the supply air outlet (24) into the room (21) and back through the return air damper (26) into the HVAC unit return air inlet (27); and wherein the ceiling air damper (25) is closed and a plenum air inlet (31) is opened, permitting lamp heat (17) in plenum (19) to convect in through the plenum (19) and through an exhaust/return air damper (29) to be exhausted through the plenum exhaust duct (30); and alternatively, a FAN ONLY mode may be used to assist convention with minimum power consumption.
 7. An integrated lighting and air conditioning system according to claim 4, operating in an OFF mode in cool weather in which: while the thermostat (16) is in the OFF mode a central computer (40) closes a ceiling air damper (25), opens a plenum air inlet (31) and opens a room air return damper (26); wherein a blower (28) of the HVAC unit (15) is OFF, permitting air from the supply air outlet (24) to convect upwards into said room (21) and enter said return air inlet (27), to cool and subside back through the HVAC unit (15), down and through the supply air outlet (24) and into the room (21); and wherein said ceiling air damper (25) remains closed and plenum air inlet (31) is opened, permitting the lamp heat (17) in the plenum (19) to convect through said the plenum (19), through an exhaust/return air damper (29) to block plenum air from entering the HVAC return air inlet (27) and be exhausted through the plenum exhaust duct (30); and alternatively, a FAN-ONLY mode may be used to operate the fan at a low flow rate to assist convection with minimum power consumption.
 8. An integrated lighting and air conditioning system according to claim 4, operating in a HEAT mode in which: while a the thermostat (16) is in the HEAT mode, a central computer (40) opens a ceiling air damper (25), closes a room air return damper (26), opens an exhaust/return air damper (29) to the return air inlet (27), and closes an exhaust/return air damper (29), to the return air inlet (2), precluding flow through a plenum exhaust duct (30); whereby a blower (28) of the HVAC unit (15) circulates warm air through the return air inlet (27) and further heats and circulates heated air through the supply air outlet (24) into the room (21) and back through the open ceiling air damper (25) with plenum air inlet (31) closed, whereby warm room (21) air receives lamp IR heat (17) in plenum (19) and passes through exhaust/return air damper (29), which is closed to plenum exhaust duct (30), and open to return air inlet (27), whereby warm room air is re-heated by the lamp IR heat and re-circulated by the blower (28) into the room (21).
 9. An integrated lighting and air conditioning system according to claim 4, operating in an OFF mode in warm weather in which: while the thermostat (16) is in the OFF mode, a central computer (40) opens a ceiling air damper (25), with a plenum air inlet (31) closed, and opens a room air return damper (26); wherein a blower (28) of the HVAC unit (15) is OFF, permitting air from the supply air outlet (24) to convect upwards into the room (21) and back through the return air damper (26) into the HVAC unit return air inlet (27), and to subside from the return air inlet (27) down and through the supply air outlet (24); or alternatively, a FAN-ONLY mode may be used to operate the HVAC fan at a low flow rate to assist convection with minimum power consumption; and the ceiling air damper (25) is opened and the plenum air inlet (31) closed, permitting lamp heat (17) in the plenum (19) to convect through the plenum (19), through an exhaust/return air damper (29) to be exhausted through the plenum exhaust duct (30).
 10. An integrated lighting and HVAC system for one or more rooms, each room (21) being connected to at least one HVAC unit (15) through one or more supply air outlets (24) and return air inlets (27); a heat-insulating divider (20 a) separating each respective room from a non-air-conditioned space (19 a); at least one lamp (18) in a fiber optic projector (1) mounted in said non-air-conditioned space, said lamp emitting lamp heat (17) into the non-air-conditioned space, wherein said heat may be vented out of said non-air-conditioned space through at least one exhaust duct (30); said lamps (18) emitting only visible light without heat (23), through integral thermal barriers (22) in the form of thermal filters and optical fibers (2) emitting light into room (21) through fiber optic luminaires (3); and a thermostat controlling the temperature of heated or cooled air passing through supply air outlet (24).
 11. An integrated lighting and HVAC system according to claim 10 in which the environmental sensor inputs (42) are selected from the group including: room occupancy, room temperature, room humidity, plenum temperature, light status, outside air temperature; and HVAC (41) performance feedback data is selected from the group including input air temperature, supply air outlet temperature, heater temperature, chiller temperature, air outlet humidity, air velocity and HVAC line voltage.
 12. An integrated lighting and air conditioning system according to claim 10 in which the thermostat (16) is one of a number of inputs to a central computer that controls the HVAC (15) unit and remotely-operated air duct dampers.
 13. An integrated lighting and air conditioning system according to claim 10 in which the lamp thermal barrier (22) of each fiber optic projector is disposed between the lamp (18 and ther optical fibers (2).
 14. An integrated lighting and air conditioning system according to claim 10 in which the lamps (18) are fiber optic projectors (1) in the non air-conditioned space (19 a), wherein the heat-insulating divider (20 a) is a side wall of the room (21), the non air-conditioned space is a utility area or closet adjacent to the room, and optical fibers (2) transmit light from projector (1) to fiber optic luminaires (3) in optional locations.
 15. An integrated lighting and air conditioning system according to claim 10 in which the lamps (18) are fiber optic projectors (1) in the non air-conditioned space (19 a) comprising a utility area or equipment closet adjacent to the room, and also housing one or more HVAC units (15).
 16. An integrated lighting and air conditioning system according to claim 1 or claim 4 in which the lamps are attached to a generally horizontal surface supported from a pair of parallel suspended-ceiling T-bar runners that also support a dual-surface light-transmitting lens assembly beneath said lamps.
 17. An integrated lighting and air conditioning system according to claim 1 or claim 4 in which the lamps are attached to a generally horizontal surface supported from a pair of parallel suspended-ceiling T-bar runners that also support a dual-surface light-transmitting lens assembly beneath said lamps, said dual-surface lens having an air space between the two lens surfaces. 